Other Agencies Required: Hydro
Pumper 114 arrived to smoke visible exiting basement windows of a townhouse. Squad 114 entered into the dwelling unit to complete a primary search and extinguished a small fire. Further scene examination revealed that a 50-foot, 16 Gauge Light Duty extension cord was powering a 1500 Watt space heater. Competent ignition source was determined to be the extension cord. Fire extended to clothes that were lying on top of the cord and spread to the adjacent couch and furniture. Estimated damage is approximately $30,000.